Modern data centers are significantly different from early versions of this method of installing servers and other equipment. The original data centers were established in the 1990s and relied on Internet connections as their foundation. Large data halls were built primarily as a space perfectly protected in terms of security, uninterrupted power supply and with adequate capacity of communication lines, mostly optical. The individual cabinets were then leased to users for their technical and Internet applications. These centers almost always had raised floors with high loading, beneath which all cabling and cooling systems were installed. Cooling was mostly centralized, so the entire room was air conditioned regardless of the distribution of the thermal load, and without the ability to effectively regulate cooling for each cabinet or the data hall.
With advancements in telecommunications, new protocols and an increase in the transmission line capacity, high-speed connections became available without the need to place the device directly onto the backbone connections. Additionally, another revolution took place on another front – processing power and storage capacity. Processor performance improved dramatically, multi-core processors were introduced, along with new operating systems. Hard drives and other storage media multiplied in capacity. Server operating systems began utilizing available resources for sharing multiple, simultaneously running applications, paving the way for virtualization – running multiple operating systems on a single physical computer.
Nowadays, many companies run their applications either on dedicated servers for specific purposes or by utilizing popular virtualization and cloud-hosting services. Both of these methods require high-density computing power. Because running businesses and institutions is a critical application, it requires power-fail safety, physical protection, and also controlled cooling. All these aspects are covered by the concept of a data center. Over time, the standard was set for the design and construction of data centers.
Cabinets are placed in groups, usually in the form of two rows spaced 1,200 mm apart (two standard raised floor tiles). The aisle between the cabinets is then roofed and closed at the ends by sliding doors. Larger data centers may feature dividing doors within these units, creating smaller sections. The main product of our company’s data center solution are data high-load data cabinets (from 1200kg to 1800kg), accompanied by other components, such as aisle roof of different types, self-closing sliding aisle door, blanking panels etc. Cabinets can be colocated (divided into multiple sections) with variety of front and rear door, locks, and other functionality.
In case it is not possible to use a raised floor (low room height, low permissible floor loading and so on) we offer an alternative solution in the form of In-Row cooling units with top media inlets and condensate pumps. This advanced solution provides a small footprint while delivering a large cooling capacity.
This critical stage of building data centers has an indefinite solution. It depends on the cabinet arrangement, distribution of heat load and its size, the choice of thermal scheme (such as hot/cold aisle or zonal distribution of cold) and many other aspects. When selecting the most suitable arrangement, it is necessary to take into account the type of cooling system (under-floor cooling, In-Row cooling units …) and with regard to the coolant used, also selecting the outer part of the system. The choice of the cooling medium should consider outdoor climatic conditions, the distance between the data center and external units, and the elevation difference between them. Depending on these conditions, we can choose water cooling with an appropriate addition of antifreeze, or a system operating with liquid refrigerant gas.
To ensure safety and redundancy for service operations, the complete system must be properly designed, both inside the data center and in terms of radiators or condensers. Furthermore, it is necessary to consider humidity control. Humidity levels below 30% pose a risk of damage to installed equipment due to static electricity surges, while high humidity can lead to condensation.
In our portfolio, you can find the cooling systems of leading manufacturers with extensive experience in data centers and telecommunication equipment cooling. Thanks to our close cooperation and support from their development teams, we can provide proven and guaranteed solutions. Designing functional, reliable, financially and operationally economical cooling systems for data centers is not an easy matter. However, our team of specialists is fully available to recommend the optimal solution based on investment and operating costs.
Manage Cookie Consent
To provide the best experiences, we use technologies like cookies to store and/or access device information. Consenting to these technologies will allow us to process data such as browsing behavior or unique IDs on this site. Not consenting or withdrawing consent, may adversely affect certain features and functions.
Functional Always active
The technical storage or access is strictly necessary for the legitimate purpose of enabling the use of a specific service explicitly requested by the subscriber or user, or for the sole purpose of carrying out the transmission of a communication over an electronic communications network.
The technical storage or access is necessary for the legitimate purpose of storing preferences that are not requested by the subscriber or user.
The technical storage or access that is used exclusively for statistical purposes.The technical storage or access that is used exclusively for anonymous statistical purposes. Without a subpoena, voluntary compliance on the part of your Internet Service Provider, or additional records from a third party, information stored or retrieved for this purpose alone cannot usually be used to identify you.
The technical storage or access is required to create user profiles to send advertising, or to track the user on a website or across several websites for similar marketing purposes.